Reasons and solutions for the hot and cold water in the bath centerIt is a very common way to use air source heat pumps in bathing centers, but what if there is a sudden hot and cold situation?
There are several factors, 1. Whether your cold and heat sources (cold water source and hot water source) are synchronized; 2. It is the water conservancy pipe network, because the usual water network is not made by you, they will not calculate the water flow and hydraulic balance . Most of the current practice is to come down from a supervisor and branch to the nearest branch. If each shower is open, this will cause hydraulic imbalance.
Two solutions: 1. The design of the pipeline, make a closed loop, for example, the water comes in from here and walks in two ways. After walking, it merges over there to form a cycle; 2. It is the change of the pipeline. Because of multiple showers, the pipe diameter may be inconsistent. Diameter reduction is very important. The hot and cold water is synchronized, and the booster pump is also synchronized. Some people also use thermostatic valves, but thermostatic valves have high requirements for water quality. If the water network is done well, there is no need to worry. In addition, it is best to separate the water in the bathroom. For example, for household hot water, the water in the bathroom basically accounts for 50%. If it is not separated, it is prone to imbalance in the water.
Leomon is a professional manufacturer of air source heat pumps. If you have any problems in the process of using the air source heat pump. Please contact us in time. Leomon will give you the best answer